Beautiful rental property requires immediate wastewater treatment solutions.
Park House Farm is a grade 2 listed farmhouse located near Keynsham, Somerset. WCI was called because the existing septic tank was constantly backed up and it was impossible to flush the toilets. Not the ideal situation with new tenants about to move in!
When WCI visited Park House Farm, we found that the septic tank was surcharging because the existing drainage field could not function given the heavy clay soils. To make matters worse, there was no watercourse near the house. And if that wasn’t enough, a rainwater drain was flooding the backdoor.
To solve the problem, a new sewage treatment plant was installed and the treated effluent plant pumped to a large drainage field in a field above the house.
The flooding at the back door was worse than expected. Not only did the surface water drain go nowhere (no wonder that it was flooding the back of the house) but the field land-drains were also flooding the back garden. To solve this, a new surface water pump station was installed with a land-drain through the back garden to take both the rainwater and the surface water from the garden. This was pumped to a new French drain in the field which discharged to a field boundary ditch.
WPL Diamond DMS2
Separate pump chamber with automatic Lowara DOC 7 submersible pump
Surface water pump station with bespoke submersible pump
High level alarms & control panel
Toilets that flush, a garden that doesn’t flood and a happy client and tenants. All the works were completed within 2 weeks of our first visit.
If you have any questions about the information presented in this case study, or you would like to talk to us about your off mains drainage options, please contact WCI on 01984 623404 or via the contact form below.
Please complete the form and a member of the team will be in touch shortly
If you have any questions or just need some clarification on the regulations and how they apply to your property, please call us on 01984 623404